Bry-Airs BryXchange is an air to air rotary heat exchanger which recovers energy from high temperature exhaust air. Considerable high temperature air is generated in kilns, ovens, furnaces etc which generally goes waste. Through BryExchange this sensible waste energy can be recovered from the exhaust air and transferred to the low temperature supply air with efficiency of upto 75% energy.
Principle of working for BryXchange Air to Air Rotary Heat Exchanger
BryXchange rotor is installed between the high temperature exhaust air and supply air stream. As the rotor slowly rotates, sensible heat of temperature exhaust air is carried over by the rotor to the low temperature supply air.
Design and Structure of BryXchange Air to Air Rotary Heat Exchanger
The BryXchange rotor has a fluted media, fabricated with material having a high heat carrying capacity, which rotates between two side-by-side ducts: on a low temperature supply air duct, the other a hot temperature exhaust air duct. The axis of the rotor is located parallel to, and on the partition between, the two ducts.
BryXchange Air to Air Rotary Heat Exchanger’s Advantage
Higher energy recovery
Lower electric energy costs
Compact unit design results in less weight
Considerable primary fuel saved
High efficiency and reliability
Stainless steel, double walled, insulated casing
Sectorized Wheel for ease of installation and maintenance
Designed for very slow rotational speed of around 8-10 RPM
Manual cleaning system for media cleaning
Heat-stabilised external bearings with teflon gasket
Smooth surface to ensure minimum vertical runout
The rotor is made of alternate flat and corrogated foil of very uniform pitch and height
Rotor depth 200mm
Substrate-Aluminised steel or Stainless Steel foil